Inflatable Air Blower (YYF)
|FOB Price:||US $19 / Piece|
|Min. Order:||20 Pieces|
|Min. Order||FOB Price|
|20 Pieces||US $19/ Piece|
|Payment Terms:||L/C, T/T, Western Union|
- Model NO.: YYF
- Pressure: 1100-3260PA
- Power: 0.18kw-3kw
- Air Flow: 420-2600CMH
- Trademark: YUTON
- Origin: Foshan, Guangdong, China
- Usage: for Air Conditioner
- Certification: CE
- Revolution: 2800rpm
- Cooling Method: Direct Cooling
- Specification: GB/T137274-9
- HS Code: 8414599099
Structure of Blower
Aluminum housing air blower consists of air outlet, aluminum impeller, aluminum housing and motor. Cold-rolling steeling housing air blower consists of cold-rolling steel air outlet, cold-rolling steel impeller, cold-rolling steel housing and motor.
Impeller: Boundary for blades of impeller is semi-open type, the surface is processed by file finishing, the impeller is adjusted by static balance and dynamic balance, and it has the characteristics of good aerodynamic performance and run stable.
Housing: Adopt aluminum alloy casting arc air inlet, the housing is convergence streamline over-all structure, fixed in front shroud with bolts. The volute of housing adopts new type noise elimination structure, has good performance for noise elimination.
Installation and maintenance
1. Installation: Install the blower according to the size and position as shown in drawing, the sundries is not allowed to remain in the housing, keep the levelness for the fan, ot only junction surface for fan and foundation, but also the joint of ducting for air inlet should be adjusted to be connected naturally, but can not be connected forcedly, can not put the weight of ducting into the fan, must ensure the horizontal position of fan.
2. Operation: After installation, the fan must be passed inspection then try the fan. The fan starts in the condition of the valve closing, prevent the motor is broken in the result of overload. New installed fan or repaired fan can not be trial operated in full more than 2 hours in full load. In the procedure of open fan, stop fan or operating, if find abnormal circumstance happen, must stop to maintain
3. Maintenance: Maintain the fan when stop the fan and insure the staff and equipment safe. Repaired fan must trial operates then put into operation, Remove the dust or other impurity in indoor of fan at fixed period. If the blower is used for lampblack exhausting in kitchen or spray, usually, the impeller should be washed in 60 days, or the impeller is overload to cause motor broken.
(m 3 /h)